Complex for the control of local process SLUP
Device has been made two-part. Part electronics has been built in in the thermostat Pixsys ATR610. The second part has the commanding panel. Complex uses on two bake for the ceramics on who has been built in the thermostat Pixsys ATR610. Makes possible the automation of work bake. When the one furnace finished SLUP complexes on her has switched on the fan for the cooling and transfer the signal for the start on SLUP complex on the second bake. This second SLUP complex start process simulating the pressing push button start. When the finished other furnace SLUP complex on her also has switched on the ventilation for the cooling and gives the signal for the starting of first bake.
Conception of complex: built-in electronics supervise the showing display and turn on signal small lamps. Status of states of indicators transfer the serial communication on the small outer console. The external console makes possible the user that chooses the way of work and manually switching on the additional heating or coolings. Across the feedback serial communication external console can the started process on the thermostat.
Picture the built-in complex in the regulator Pixsys ATR610
Characteristic of complex for the supervision showings display:
Supervises the 4 multiplexed displays and 5 multiplexed the LED (represent the additional multiplexed digit) 8 digital entries for the segment and two entries for the syncronization
Frequency of multiplex 2ms / digit (1ms minimally)
Production of status comparison of specified samples (e.g. the determined message, blinking LED, etc)
Communication 19200 bauds optically is separated (the status displays or complete contents)
Complex owns three the digital output which can simulate the work push button (across ULN2803 on the mass)
Digital filtrations of samples supervise prevent possible errors (necessary e.g. 3 same cycles on the display in order to the complex accept the presentation)
The possible use:
Complex it possible install on the every multiplex display for the purpose of the displayed signals. Thus it possible make the comparator to the values and e.g. from indicators of values get the regulator or implement the alarm function on the regulator which has had. Counter displays may be and greater than 5
The serial communication was able will substitute with the optic isolated input and output.
The other part SLUP automatics is the command panel with signal LED to the diodes and push button for the control. Complex has the entry for the serial communication with board built-in in Pixsys kontoler (" TX1 "), entry for the external start, optically the separated output for the starting (" finished ") also the output for three 12V relays (the fan, heater and finished). Relay " Finished " activated at the same time when and optic output " finished ". Contacts of relays use for the signalization personnel which operates at furnace.
All states note in serial EEPROM also the panel wakes up in the last set state.
Price for two sets with the implantation in (without the travel expense): 7200kn
Price with the other application: on the inquiry